480 x 272 Pixels TFT-Display
Saia PCD® 4,3" Room Web Panel with
System Catalogue : Control Panels HMI
|Extract||26-215_A0200||System Catalogue : Control Panels HMI|
PCD7.D443WTPR / PCD7.D443WT5R
|Datasheet||PP31-025||PCD7.D443WTPR / PCD7.D443WT5R|
PCD7.D443WTxR Room Web Panel
|Manual||27-644||PCD7.D443WTxR Room Web Panel|
EPLAN product macros, DWG and DXF files can be found here.
Firmware used in production
The actual COSinus FW 1.28.xx or higher is available from the COSinus firmware page.
Good to know
- The mounting frame of the PCD7.D443WTPR/PCD7.D443WT5R which is supplied together with the hardware version A can't be used for the devices from the hardware version B or later.
- The temperature sensor which is integreated in the the device is avilable since the hardware version B
- To support the temperature sensor at least the firmware version 1.28.04 is required
PCD7 / D443WT5R
Are devices or software developed from Saia-Burgess Controls affected by the Domain Name System (DNS) vulnerabilities, published with the report name NAME:WRECK? (FAQ #102046)
Saia-Burgess Controls devices and software are not affected from Domain Name System (DNS) vulnerabilities published with the report name NAME:WRECK
Why the P-Web panel PCD7.D44WT5R crash/reboot if the user access the setup menu? (FAQ #102022)
If the user want to access the setup menu of the P-Web panel, then it’s possible that the application program on the P-Web panel crash/reboot and the access to the web-page is no more responsive.
The problem occurs only if the user want to access the setup menu and if the user has set a password to access the setup menu and uses the software watchdog on the application program.
This issue is caused when the setup menu of the P-Web panel is password protected and a software watchdog is implemented in the application program.
Depending of the used firmware, the combination of those two points cause the panel to:
FW version behaviour FW =< 1.28.11 P-Web panel freezes, program stop working until a power FW>= FW 1.28.22 P-Web panel does reboot, also the application program does reboot
every time the users want to open the setup menu while application program is running.
The solution consists to increase the timeout time for the software watchdog to 800ms.
Opening the setup menu on the P-Web panel slows down the program in that way that the software watchdog is executed and the whole P-Web panel is rebooted.
To avoid this, the system watchdog time has to be increased.
This can be done over a CGI instruction or IL programming.
The CGI instruction has to be done over a Web-Browser and the P-Web panel should be available via LAN, with a IP address.
FW 1.28.22 or newer must be used.
Workaround with CGI instruction.
1. Be sure to have a ethernet connection to the P-Web panel
2. Open the web-browser and execute the CGI command:
3. Control if the set settings are been set correctly:
4. To save the configuration the following command ha to be executed:
When it is not saved, the setting will go back to default when the controller does as restart.
Attention: This command should be used exclusively in this case.
Workaround for IL programming:
Use the IL instruction 'SYS.WriteTag' to set the software watchdog to 800ms.
CSF S.SF.SYS.Library ;Library number
S.SF.SYS.WriteTag ;Write Tag
Watchdog_R_name ;1 X|R IN, Registry name
Watchdog_T_name ;2 X|R IN, Tag name
Watchdog_value ;3 R|K IN, Tag Value parameter type
Watchdog_value ;4 X|R IN, Tag Value
Program_Status ;5 R OUT, Status
The IL program is attached to this FAQ and can be added to the PG5 project by using the function
'Program files, Add Files'
Do not set the software watchdog value differently as described since it could damage the P-Web Panel.