The requested software / document is no longer marketed by Saia-Burgess Controls AG and without technical support. It is an older software version which can be operated only on certain now no longer commercially available products.
Room Control Panel (obsolete)
PCD7.L290 Individual Room Control Panel
|Technical Info||PP26-454||PCD7.L290 Individual Room Control Panel|
Graphic terminal PCD7.D290
|Manual||26-841||Graphic terminal PCD7.D290|
HMI Editor 14210 and Library update 14211 for PCD7.D290
|Software||HMI Editor 14210 and Library update 14211 for PCD7.D290|
The version of PG5 1.4 200 doesn't contain the latest HMI Library needed for programming the PCD7.D290 Display.
Unzipp the attached file and run the 2 exe files (HMI editor 14210 and library 14211)
Don't apply these files in case PG5 1.4.30
Good to know
The PCD7.D290 has been discontinued in 2010 without replacement. The repair service is guaranteed until end of 2013.
PCD7 / D290
Experiences made with the internal sensors of the PCD7.D290 display (FAQ #101360)
When using the internal sensors of the PCD7.D290 it has been noticed that the the pratical measurement accuracy is below the indication of the corresponding manual (26/841).
Due to the fact that the sensors are mounted directly in the display which itselfs influences the measurement it has been stated that the precisision is not according to the manual of this PCD7.D290 display (26/841 version 4). The chapters 4.2.3 (Temperature sensor) and 4.2.4 (R.H. sensor) will be adapted accordingly in the next release.
4.2.3 Temperature sensor
Temperature sensor used in PCD7.D290 is active and supplies as output a voltage of 10.0 mV/°C; this sensor is directly calibrated in °C.
Embedded temperature sensor component is directly soldered on the main board of the PCD7.D290
Theoretical accuracy value: ± 0.5°C at 25 °C., Practical accuracy value: ± 1°C (± 1.5°C in the worse case)
4.2.4 R.H. sensor
R.H. sensor used in PCD7.D290 is capacitive and supploes as output a capacity in the range 161.6 pF at 0% R.H. and 193.1 pF at 100% R.H.
The evaluation algorithm is stored directly inside D290 firmware.
Embedded humidity sensor component is directly soldered on the main board of the PCD7.D290 --> Practical accuracy value: ± 5%
Communication in Bus Terminal topology doesn't work on PCDx.F2xx Module! (FAQ #101091)
When more than 1 displays of the same type (PCD7.D23x and PCD7.D290) are connected to a RS 485 port (Bus terminal) of a PCDx.F2xx module, the communication doesn't work. Only one of the displays is available, the other one(s) is (are) not accessible!
The ports 100 to 131 available on the PCDx.F2xx modules have different timing properties and are therefore not appropriate for PCD7.D23x and PCD7.D290 in bus terminal topoloy!
Use another RS 485 port (onboard or with F1xx).