Welcome to the support site
If you know our products and are looking for technical information you are at the right place here.
If you want to get an overview about our company, news and events please refer to www.saia-pcd.com.
System Catalogue 2022/2023
A quick way to get an overview about our product range is to consult our system catalogue PLC, DDC, HMI, Web& IT
Security Upgrade for PCD Controllers
New Firmwareversions offering improvements in IT-Security for PCD Controllers are ready to download. >> More Infos
Connection of PCD controllers directly to the Internet
Reduce the risk of potential intruders in automation systems. Take appropriate protective measures in your PCD control. >>More Infos
Last changes to this site
Firmware 1.08.06 for PCD1 E-Line RIO's L-Series is available on the support homepageMonday, 19. June 2017
Firmware 1.08.06 for E-Line RIO's L-Series:
is available on the support homepage
This Firmware supports S-Bus or Modbus Telegrams on the RS485 serial interface.
For the configuration of the RS485 serial interface for Modbus communication it’s necessary to use the E-Line RIO configuration App.
The E-Line RIO configuration App allows to define the S-Bus or Modbus station address of the device between 0 and 253.
S-Bus communication stops when S-Bus communication library 2.7.370 or E-Line S-Bus communication library < 1.2.110 was used and the communication mode ‘on Event’ or ‘on Sampling time n’ has been selected on the S-Bus communication FBoxesMonday, 12. June 2017
Due to an error on the S-Bus communication library 2.7.370 and the E-Line S-Bus communication library < 1.2.110, the S-Bus communication stops after a certain time or after download of the program, if the communication mode ‘on Event’ or ‘on Sampling time n’ has been selected on the S-Bus communication FBoxes.
To solve the issue, either configure the communication mode in the ‘old’ FBox to ‘On each cycle’ or ‘on data change’ or use the E-Line S-Bus communication library 1.2.110 and the S-Bus communication library 2.7.380 or newer ones.
PG5 2.2.230 is available on the support homepage as well in the SBC PG5 update managerFriday, 05. May 2017
PG5 2.2.230 can be downloaded from the support homepage as well in the SBC PG5 update manager.
Information's about the modification are available on the support homepage or from the document 'What's new in PG5' (in English) or in German 'Neuerungen in PG5 V2.2' or in French 'Nouvelles fonctionnalités du PG5 V2.2'.
COSinus maintenance Firmware 1.28.11 with BACnet Rev.14 support for PCD1.M2220-C15, PCD1.M2160, PCD2.M4x60, PCD3.Mxx60, PCD3.M6880 are available on the support homepage as well in the SBC PG5 update managerFriday, 07. April 2017
This COSinus maintenance Firmware 1.28.11 do support the BACnet Rev. 14 an can be used on the following systems:
and BACnet firmware 1.28.11 for this PCD's
The firmwares available on the support homepage as well in the SBC PG5 update manager.
This firmware should only be used if BACnet Rev.14 is required in the application.
To use BACnet Rev.14 it’s necessary to use PG5 2.2.220 or newer.
COSinus Firmware 1.26.28 for PCD1.M2220-C15, PCD1.M2xx0, PCD2.M4x60, PCD3.Mxx60, PCD3.M6880, PCD3.T66x are available on the support homepage as well in the SBC PG5 update manager.Friday, 07. April 2017
COSinus Firmware 1.26.28 for:
and BACnet and LonIP firmware 1.26.28 for this PCD's
are available on the support homepage as well in the SBC PG5 update manager.