It’s possible to set the triac output Y1/Y2 of the PCD7.L60x-1 Room controller as 2 point output?
Yes it’s possible to use the Y1/Y2 triac output as 2 point outputs (always off / always on) instead as PWM outputs.
To use the outputs Y1/Y2 as 2 point outputs it’s necessary to define the configuration of the output Y1/Y2 “unused” in the configuration F-Box of the PCD7.L60x.
With the help of the F-Box ‘Analog Output’ from the F-Box family 'RoomControler PCD7_L60x' it’s then possible
to set the output Y1/Y2 of the PCD7.L60x to:
|Status of the output ||Value to be written |
Use only the value 0,0 or 100,0% to switch off or on the Y1/Y2 outputs.
Any other value between 0.0 and 100.0% does set the output in the PWM mode.
PCD7 / Lxxx
Last update: 20.04.2015 12:57
First release: 27.10.2014 14:25