AWD3/ALE3/ALD1 energy meter with serial interface (for example S-Bus): What happens if the direction of the current is inverted (from Lx output to Lx input)?
If the current direction is inverted, for example if a PV installation does supply back the current, then the active power and the cosine Phi of the concerned phase on the AWD3/ALE3/ALD1 will have a negative sign.
The current is always displayed without sign (positive).
Behavior of the kWh counter:
In case of a non-bidirectional meter, the meter will display an error on the concerned phase and will not increment nor decrement the kWh counter with the measured power.
In case of a bidirectional meter, the meter will not display an error and will increment the corresponding kWh counter with the measured power.
CC Control Components / AAE3 / ALE3 / AWD3
CC Control Components / AAD1 / AAE1 / ALD1
Last update: 27.05.2015 07:16
First release: 22.04.2010 07:09