How can local SBC hardware be projected in Simatic-Manager?
Local SBC hardware (I/O modules) is configured with the I/O Builder. Then the I/O Builder is used to generate an STL source, which is imported into the S7 project and compiled. The hardware configuration is therefore defined in a data block (DB1, DB 511 or DB 1023). When reconstructing or modifying the HW configuration, a PCD restart (Stop/Start) is always required. The I/O Builder can be downloaded free-of-charge from Internet address: www.sbc-support.ch/overview/xx7Configuration.htm
xx7 Series / Hardware configuration
Last update: 24.05.2015 04:53
First release: 08.06.2004 13:45