Sensors on Belimo MP-Bus don't show the correct values
Belimo MP-Bus actuators produced bevor 03.05.2005 can show this problem.
This is an Problem of the actuator. If you have mixed active, passive and switched sensors on the Belimo MP-Bus actuators, it can happened that the displayed values measured over the MP-Bus are not correct.
If you have connect an switch sensor on the MP-Bus device adressed MP3 all the measured values can be wrong. This problem is fixed in all the actuators produced since 03.05.2005.
Don't use the MP-Bus adress MP3 for switching sensors.
Third Party Products
PG5 2.0 / MP-Bus
Last update: 25.05.2015 21:57
First release: 22.06.2005 07:06